A vulnerability has been identified in Firmware variant IEC 61850 for EN100 Ethernet module (All versions < V4.33), Firmware variant PROFINET IO for EN100 Ethernet module (All versions), Firmware variant Modbus TCP for EN100 Ethernet module (All versions), Firmware variant DNP3 TCP for EN100 Ethernet module (All versions), Firmware variant IEC104 for EN100 Ethernet module (All versions < V1.22). Specially crafted packets to port 102/tcp could cause a denial-of-service condition in the EN100 communication module if oscillographs are running. A manual restart is required to recover the EN100 module functionality. Successful exploitation requires an attacker with network access to send multiple packets to the EN100 module. As a precondition the IEC 61850-MMS communication needs to be activated on the affected EN100 modules. No user interaction or privileges are required to exploit the security vulnerability. The vulnerability could allow causing a Denial-of-Service condition of the network functionality of the device, compromising the availability of the system. At the time of advisory publication no public exploitation of this security vulnerability was known.
Published : 2018-07-23 21:29 Updated : 2019-03-22 17:29
CVSS Score More info
Score 7.8 / 10
A vulnerability exploitable with network access means the vulnerable software is bound to the network stack and the attacker does not require local network access or local access. Such a vulnerability is often termed "remotely exploitable". An example of a network attack is an RPC buffer overflow.
Specialized access conditions or extenuating circumstances do not exist. The following are examples:
- The affected product typically requires access to a wide range of systems and users, possibly anonymous and untrusted (e.g., Internet-facing web or mail server).
- The affected configuration is default or ubiquitous.
- The attack can be performed manually and requires little skill or additional information gathering.
- The race condition is a lazy one (i.e., it is technically a race but easily winnable).
Authentication is not required to exploit the vulnerability.
|Siemens||Dnp3 Tcp Firmware||-||cpe:/o:siemens:dnp3_tcp_firmware:-|
|Siemens||Modbus Tcp Firmware||-||cpe:/o:siemens:modbus_tcp_firmware:-|
|Siemens||Profinet Io Firmware||-||cpe:/o:siemens:profinet_io_firmware:-|
History of changes